|Place of Origin:||China|
|Model Number:||JBNG Series|
|Trade Terms:||FOB, CFR, EXW, CIF|
|Min. order:||1 Pieces|
|Cooling Method:||Direct Cooling|
|Category:||Plastic Rolling Machinery|
|Payment Terms:||L/C, T/T, D/P|
Industrial Cooling Tower (JBNG Series)/cooling tower/Chinese cooling tower
1. Cooling capacity for one cell is from 800 to 4500m3/H, relevant refrigeration ton is from 1180 to 6640. Several cells can be fixed together.
2. Body frame:
JBNG series: Made up by steel bar, round and square steel pipe. All components are hot DIP galvanized or handled with other special embalmment. Thus it is anticorrosion and high intensity.
3. Casing: Made of reinforced compound material. The body surface is imported colorized gel-coat surface, which contains ultraviolet radiation absorbefacient.
4. Drive system: Use horizontal shaft drive gear reducer. For easier maintenance,
5. Distribution system: Use distribution pipe fixed with advanced gravitational nozzle in the world. It may work at low water supplier pressure, sprinkle water equally, and never jam.
6. Sprinkling fill: Use high efficient PVC fill. The piece mould is tested by authority department, compared to other fill, it has such advantages as larger surface, small air resistance, good hydrophile, large heat transfer coefficient, firm assembly,
7. Eliminator and louver: Use national advanced special three-dimensional eliminator, impact of which is rather remarkable, with drift loss of less than 0.005 percent.
Fan stack is made by high strength composite, kinetic energy of which can be reclaimed.
8. Guarantee of cooling capacity: Designed strictly on GB 7190.2-1997 and advanced design idea in the world; Tested in Jinling Thermal Performance Test Lab, which is built on CTI standard. Production is controlled and guaranteed by ISO9001 and ISO14001.
9. Jinling shall provide:
1). The entire steel frame above cold water basin. If customer need fibre cold water basin, he shall state before place order, and the price will be recalculated.
2). FRP fan stack, side casing, top casing and partitions.
3). Sprinkling fill
5). Fan and motor
6). Inside water distribution pipe and sprinkling nozzle
7). Water inlet flange (valve and up- down connection pipe not included)&